Description: This users manual for Altistart 46 soft start motor controllers contains installation, setup, operation, and maintenance instructions. User’s manual ATS46, 9/21/18, English, Spanish, French, pdf MB. Data Bulletin. Cross Reference Guide for ALTISTART® 46 Soft Start Motor. User’s manual UNI-TELWAY ATS VW3G, 12/13/17, English, pdf MB. Programming manual ATS VW3G, 12/13/17, English.
|Published (Last):||18 March 2006|
|PDF File Size:||2.81 Mb|
|ePub File Size:||3.50 Mb|
|Price:||Free* [*Free Regsitration Required]|
Altistart 46 Soft Starters – Documents and Downloads | Schneider Electric
The motor does not brake the load correctly The motor does not brake the load correctly cause check remedy High inertia After the brake request, there is current into the motor even in a discontinuous way. Their value is calculated to obtain rated current of each coiling for primar y rated voltage.
Phase rotation fault assignment Function Phase rotation detection PiF Phase rotation state The function is active at each start order.
During a start-order on contactor with software version inferior to V1. SY3KC 2 Black wires marks 14 and Network Function Phase fault Phase fault This phase fault can be generated by two sub-defects: Recommended torque load for screw M4: DZ4DP 16 2 Black wires marks 16 and The following instructions have to be performed: InF recognition of rating Up to now experience: For wiring J12 and J32 use long cables with connectors so that they can be connected to the plug-in unit furthest to the left of the starter.
Assembly size 1 Parts list Part 2: Starting end on a high inertia, low opposing torque application. It is also possible to know the software version with PC software. J7 Connector if pump unit J9 J10 J11 Conversion instructions for sizes 4 and 5 6 – Loosen the fixing screws of the metal support. Version Date of selling V1. Minimum resistance has to be 50 kilo-ohms. The table alyistart gives the detailed product references of the equipment necessary, according to the power of the motor in the case of normal duty.
V 2 at max vacuum 1 With rated primary voltage and rated secondary intensity.
M Has to be fixed on one of the assembling screw before soaking Red wire mark 4: J 43 Conversion instructions for sizes 4 and 5 6 – Wiring the control cables of thyristors J4 to J9. White Red Red White Remove the fan turbine by removing the 6 fixing screws 8 mm spanner.
Remove the connectors located at the base of the product. It’s a community-based project which helps to repair anything. Connect the cables to the electronic card observing the labelling and connecting the connectors with 2 wires to the card.
Altistart-« 46 Soft Start Motor Controllers Users Manual
Connect the connector of the current transformer cable to J 43 on the electronic card, observing the wire coding. Session program is included in appendix.
SY3CM Blue wire mark 3: They are also manufactured and tested at Schneider factory at Pacy Blanchet. For units with two transformers only the right-hand transformer viewing the unit from the front is to be removed.
Altistart 46 Maintenance Manual |
The time taken to perform the conversion is approximately two hours, to which site transfer time must be added. Expanded polystyrene is not allowed. It suits the one used for Altivar tests. Low torque at start tQ0. Conversion instructions for sizes 4 and 5 Remove the cable from the current transformers by cutting the clamps and unscrewing the connection screws on the transformers. Replace connectors J13 and J14 from the current transformers on the rating card.
Starter not supplied with current on L1-L2-L3. Proceeding for on-site test of characteristics dispersion of Altistart 46 thyristors leakage current: Avoid the current pulse in the engine as well as startup in current control correction of the anomaly concerning a random startup following a series of transient power cutoffs.
At each design and manufacturing step, the products are processed with great care. V Insulation varnish must comply with U.
A PC software version superior to V1. If phase rotation fault is selected, check if the phase rotation of the network manusl is in conformity with the one selected direct, indirect, otherwise, the fault is generated. Reference Rated ef f. Transformer complies with U.